This is what we understand by oil analysis service: Take an oil sample, apply the oil sampling set and then use it for analysis. The transformer insulating oil analysis starts with the correct procedure of oil sampling according to DIN EN 60422. For oil analysis it is important to select the appropriate oil sampling set. Whether aluminium bottle or glass syringes in a transport case, the oil samples are selected according to the analysis requirements. Standardized procedures such as Gas-in-Oil Analysis for the condition assessment of transformers.
The oil samples are the DNA of a transformer. There are some key gases that we look for in a dissolved gas analysis (DGA). Some other tests are also performed such as dielectric breakdown voltage, acid neutralisation number, interfacial tension or water in insulating liquids to name a few. Therefore, oil sampling must be carried out carefully
Viscosity and purity tests are important for checking lubricants. At your request, we assess operating fluids such as lubricants, oils, insulating oils, turbine oils, coolants and hydraulic oils. The oil analysis to be carried out does not end with the test results. If desired, you will receive solution-oriented assistance from us. Our know-how with quality and competence for your operational practice. If you would like to know more about these topics, visit our practical seminars.
We offer you advice on the topics of: Oil analyses | Oil ageing | Oil service.
Insulating Oil Analysis | The most important criterion of an oil-filled transformer is an intact insulation oil, thus ensuring safe operation of the transformer. Why should one carry out the oil examination of a transformer? The aging process of the insulating oil is progressing due to strong stress and thermal influences. It is recommended to take an oil sample in case of the following events: Before commissioning a new oil transformer. For regular checks during operation. In all cases where there is a suspicion of damage to the oil transformer.
In case of malfunction or when the protective devices are triggered. When taking an oil sample, some factors must be taken into account. For a transformer insulating oil inspection, it is assumed that the oil samples are filled in suitable containers. An oil sample from electrical equipment tells a lot. The oil sample serves to document trends and tests. Impurities in the oil such as particles, acid number and viscosity etc. provide information about the condition of the oil. The aim is to determine changes due to aging and to detect functional defects at an early stage. If samples are taken improperly, the resulting measurement and analysis results are invalid. Insulating Oil Analysis.
Before taking the oil sample, it must be determined according to which standard the oil sample analysis is to be performed. The quantity and also the sampling point of the oil to be extracted depends on this standard. Periodic and chemical tests as well as chromatographic analyses (Gas-in-Oil and HPLC) of insulating oil are indispensable. In order to apply the entire spectrum of oil analysis in a targeted manner, WGM Support works closely with independent laboratories.
We offer you advice on the topics of: Oil sampling | Oil analyses | Oil evaluation